Notes - please read first:
1. The unit should be installed
according to the NATIONAL WIRING code of practice, as is required in every
SPEEDHEAT is available in three sizes and is designed to operate on
a 240V power supply. The 3kW
SPEEDHEAT will draw± 15A and the 5kW SPEEDHEAT will draw 22A.
SPEEDHEAT must be solidly mounted in a fixed vertical position.
4. Ensure that the minimum of a 2.5 mm² cable is used on either
unit. Should the distance between the 5kW unit and the power source be more
than 4 metres, we recommend a 4mm cable be used.
5. To conform to safety regulations the 3.5kW and 5kW
SPEEDHEAT must be connected to an isolator/breaker providing all pole
disconnection of 20A and 25A respectively and via the earth leakage system.
6. All work carried out on a distribution board should be done by
a qualified person.